A Switch group is a logical summary of eBus or Modulbus relays. Per Location 255 Switch groups exist, at what 200 are free selectable by the user. The Switch groups 201 to 255 are used for Annunciator by the system. Each relay of a eBus device (multimess, multisio, multimax, …) can be associated to a Switch group. The association take place in the respective device properties.
Different actions affect with different priorities to the Switch groups. So a manual switch has a more important priority as a system action, for example.
|Device / system action||3|
Individual warnings or disorders always affect an additional activation of the higher group. Furthermore, for common disorders as well as common warnings exist a horn and visual indicator. To quote affects the reset of the horn. But each new report affect the horn new. The visual indicator stay active, until the problem is removed.
|255||Common alert Horn||Switch with 250|
|254||Common alert Visual indicator||Switch with 250|
|253||Hupe Sammelwarnung||Switch with 240|
|252||Common warning Horn||Switch with 240|
|250||Common alert||Switch with 249, 245, 244, 243|
|249||Common alert electr. Network||Switch with 248, 247, 246, 245|
|248||Common alert SecureF Alarm|
|247||Common alert SecureC Alarm|
|246||Common alert electr. Power|
|245||Common alert electr. Network generally|
|244||Common alert Limit violation|
|243||Common alert device problem|
|240||Common warning||Switch with 239, 238, 237, 236, 235|
|239||Common warning SecureF warning|
|238||Common warning SecureF prewarning|
|237||Common warning SecureC|
|236||Common warning electr. Network generally|
|235||Common warning device problem|